Following an in depth site survey at The Holiday Inn hotel in Bromsgrove by William Austin’s, it was concluded that the LPHW plant urgently needed replacing. Part of the remedial programme included the supply of new boiler and hot water generation plant by Mikrofill.
Specifically 4 No Ethos 130 kW wall-mounted condensing boilers c/w a Mikrovent 750low loss header & air/dirt separator were skilfully installed by William Austin’s. The works had to coincide with a tight schedule ensuring complete continuity of the hotels services. The new boiler plant with a combined modulation of 40 : 1 (520 kW to 13 kW) supplies LPHW to the pool, spa and public areas throughout the hotel.
In addition, the HWS circuit was also upgraded with the installation of 2 No Extreme 500 litre loading cylinders capable of producing in excess of 5,000 litres p/hr at 60°C. The HWS loading cylinder maximises the efficiency of the Ethos condensing boilers as the Extremes integral plate heat exchanger operates at a Delta t 30°C (80/50°C) whilst producing a total instantaneous performance of 70 l/m at 60°C.
For more information on these and other Mikrofill products please call the sales team on 03452 606020 or visit www.mikrofill.com
The Chartered Institution of Building Services Engineers (CIBSE) and the Department for Business, Energy & Industrial Strategy (BEIS) have launched new guidance AM17: Heat pumps for large non-domestic buildings....
Arup have worked as technical authors under the direction of the CIBSE Technical team supported by a Steering Group comprising industry stakeholders and representatives including developers, landlords, occupiers, designers, installers, operators, manufacturers, and other specialists.
Toshiba Carrier UK has rolled out the latest generation of its high-performance ESTIA air-to-water heat pumps operating on lower global warming potential (GWP) refrigerant R-32....