Published on 26 - April - 2012
An unregistered gas fitter has been prosecuted for illegally carrying out work on a house in Hucknall, putting residents' lives at risk.
Unregistered gas installer put lives at risk
Robert Metcalf, 54, installed a new gas boiler at the Long Hill Rise property during August and September 2009, but following problems with the new boiler the customer contacted the Gas Safe Register to check his registration status.
It was discovered that Mr Metcalf was not registered and should not have attempted to undertake such a job. The matter was passed to the Health and Safety Executive (HSE) for investigation.
HSE found there were a number of defects on the boiler. There was a lack of earth bonding, the pipework sleeve was not sealed where it passed through the wall and the flue was not sealed on the inside or outside of the building. In addition, the pressure relief discharge pipe was sited above a doorway onto a walkway which could have resulted in hot water being expelled onto the occupants.
Robert Metcalf (trading as Metcalf Plumbing), of Valeside Gardens, Colwick, pleaded guilty at Nottingham Magistrates' Court to breaching Regulation 3(3) of the Gas Safety (Installation and Use) Regulations 1998 and was fined £500 with costs of £200.
After the hearing, HSE inspector David Butter said: "At the time of carrying out the work, Mr Metcalf was not registered with Gas Safe, and some of the work carried out put residents at risk.
"In order to work legally in the UK, gas installers must be registered with the appropriate approved body. It is essential that homes and businesses check this before having work carried out to ensure the job is completed to a high standard and most of all, is safe.
"Badly fitted and poorly serviced gas appliances can cause fires, explosions, gas leaks and carbon monoxide poisoning. Our message to everyone is clear - check the engineer's Gas Safe Register ID card before letting them begin work and check the details online or by calling 0800 408 5500."
© Datateam Business Media Limited. Heatingandventilating.net news and feature articles may be copied or forwarded for individual use only. No other reproduction or distribution is permitted without prior written consent.